RS-485 to RS-232 dispenser interface converter
RS-485/RS-232 dispenser interface converter (RS-485 to RS-232 interface and backwards) is used for communication with fuel dispensers, which use RS-485 interface, through RS-232 interface, and also on the contrary: for communication with fuel dispensers, which use RS-232 interface, through RS-485 interface.
RS-485/RS-232 dispenser interface converter allows connection of up to 2 fuel dispensers.
RS485-2 (2-channel interface converter board):
Click on image to enlarge
RS485-2 (2-channel interface converter board), mounted in plastic box:
Due to a reason that RS-232 interface in accordance with its standard is applied on distances not exceeding 15 m, RS-485/RS-232 dispensers interface converter can be applied in order to enlarge this distance by converting the interface to RS-485, which allows distance for communication up to 1200 m (in accordance with its standard) and thus provide remote control over dispensers with RS-232 interface from a bigger distances.
|Power supply voltage||12 V DC|
|Current consumption||75 mA max|
|Temperature range||from -40°C to +80°C|
|Overall dimensions||85 x 58 x 25 mm|
|DATA PORT RS-232||RS-232
(3 wires: TxD, RxD, Gnd)
|Communication with a control system (POS terminal, cash register, OPT). Selection of interface is made using DIP-switch.|
|DATA PORT RS-485||RS-485
(2-wires: line A, line B)
|PUMP PORTS||Optically isolated RS-232 (3 wires: TxD, RxD, Gnd)||Connection with fuel dispensers using RS-232 interface. Separate dispensers have to be connected to each of the pump ports.|
(3 wires: TxD, RxD, Gnd)
|Update of the interface converter firmware|
Click on image to enlarge
|RS485-2 interface converter PCB board with terminal blocks
Order code: RS4852-PCB-001
|RS485-2 interface converter board, mounted in plastic box
Order code: RS4852-BOX-001
Frequently asked questions
1. What are the installation requirements for the petrol station?
WARNING! Manufacturer guarantees reliable and stable operation of products only at compliance with below requirements. In case of absence of uninterruptible power supply or incorrect wiring of products to it any claims to malfunction of software are not accepted.
1. Requirements to power supply
The described products come into structure of control system (POS) for petrol station. Power supply of the products should be done from a separate power supply with built-in filter of radio frequency interferences and limiter of high voltage pulse interferences. Power supply should have a safety factor of 1.5.
At emergency switching off the power supply or in case of power voltage exceeding its permitted ranges the products can switch off with loss or corruption of data and possible damage of hardware and software. Power supply of all electronic blocks of POS and electronic pumpheads of dispensers, which are connected through information lines, should be made from single common uninterruptible power supply source (UPS). Connection of other devices to given UPS is strictly prohibited. UPS should be of continuous action (online) and work with double conversion with output voltage regulation. UPS should have a safety factor of 1.5. Filter of radio frequency interferences and limiter of high voltage pulse interferences should be used for feeding equipment from UPS.
Supply of electronic pumpheads of dispensers should be made from the UPS unit using 3-wires scheme with isolated neutral through dedicated two-pole breaker for each dispenser. Connection of other parts of dispenser to UPS unit (expect electronic pumpheads) is strictly prohibited.
UPS unit should be connected to a separate three-pole socket fed through the three-wire feeder (phase, neutral, ground wires) with insulated neutral from a dedicated circuit breaker of switchboard. Feeder coming from the switchboard to the socket should located not closer than 0.3 meters to other feeders. The socket should be located at a distance of not more than 1 meter away from the POS. Phase wire of the feeder should not have any other consumer, which are sources of interferences (for example motors).
For protection of POS and UPS from secondary effects of atmospheric electricity it is required to install high-voltage arresters (dischargers) at the transformer substation or on poles of power lines.
2. Requirements to grounding
In the switchboard the ground wire of feeder socket should be connected to the grounding screw, which should be connected by means of welding with a protection grounding circuit of petrol station by steel wire with a diameter of not less than 5 mm.
Protection grounding circuit of petrol station should correspond to safety requirements and be separated from the station lightning protection circuit. Distance from the nearest electrode of protection grounding circuit to electrode of lightning protection circuit must be at least 10 meters. Resistance of the protection grounding circuit should be not more than 4 Ohms and must be confirmed by the test report. Length of wires from the switchboard to the nearest electrode of protection grounding circuit should not exceed 15 meters.
3. Requirements to laying of cable communications
Laying of power and information wires to dispensers should be done in separate pipes with distance of not less than 0.3 meters between each other. For informational wires (current loops, RS-485, other interfaces) it is recommended to use shielded twisted-pair cables (recommended type – FTP CAT 5E). The cable shield must be connected to the ground connector on one side only – on the side of the dispenser.
2. Is it possible to connect RS-485 to RS-232 interface converter directly to personal computer?
Yes, RS-485 to RS-232 interface converter has 2 interfaces for communication with a control system: RS-232 (3 wires: TxD, RxD, Gnd) and RS-485 (2 wires). Thus using RS-232 interface you can connect RS-485 to RS-232 interface converter to COM-port of personal computer.
3. Can the RS-485 to RS-232 interface converter convert vice versa: from RS-232 into RS-485?
Yes, conversion into both directions is supported without necessity to change anything in the converter.
4. What wires are used for connection of the RS-485 to RS-232 interface converter with dispensers? Are the wires supplied together with the converter?
RS-485 to RS-232 interface converter is supplied without cables for connection to dispensers. For connection to dispensers you will have to prepare the cablings yourself. You can use any standard FTP cable with twisted pair and aliminium foil for screening (like FTP CAT 5E) for connection.
5. How to power supply the RS-485 to RS-232 interface converter? Is the power supply source supplied together with converter?
RS-485 to RS-232 interface converter uses 12 V DC for feeding. Maximum current consumption is 75 mA.
Power supply source is not supplied together with a RS-485 to RS-232 interface converter. The power supply should be selected locally. This is connected with a reason that different countries may have different electricity network specifics: frequency and voltage.
At selection of the power supply you need to pay attention to the following 2 factors:
- output voltage of power supply should be 12 V DC
- maximum allowed current consumption of power supply should be more that maximum current consumption of the converter. If several devices are connected to the same power source - then their total current consumption should be less than maximum allowed current consumption of power supply.
6. What are connection schemes of the RS-485 to RS-232 interface converter to dispensers?
Connection schemes of the RS-485 to RS-232 interface converter to dispensers are shown in RS-485 to RS-232 interface converter technical guide, which you can download 'Downloads' section of the RS-485 to RS-232 interface converter web-page.
6. What is the communication protocol used in RS-485 to RS-232 interface converter?
RS-485 to RS-232 interface converter does not have a communication protocol. It serves for conversion of the interface and improve transmission between the control system and dispensers.
Ask YOUR questions about
"RS-485 to RS-232 dispenser interface converter"
We will gladly answer all of your questions!
Other products of section:
PTS controller over fuel dispensers and ATG systems
PTS fuel pump controller is a forecourt controller and is intended to provide simultaneous remote control over petrol, diesel, CNG and LPG dispensers and automatic tank gauge (ATG) systems installed at petrol, CNG and LPG stations and storage depots.
GB dispenser interface converter
GB 2-wire interface converters (RS-485/RS-232 to 2-wire current loop and backwards) are intended for communication with dispensers (Gilbarco, Tankanlagen Salzkotten, Batchen Email, Kraus, Prowalco, Bennett and others) using 2-wire current loop interface through interfaces RS-232, RS-485 (2 wires).
TH dispenser interface converter
TH 3-wire interface converters (RS-485/RS-232 to 3-wire current loop and backwards) are intended for communication with dispensers (Tokheim, Satam, Emgaz Dragon, Kalvacha, Kraus, others) using 3-wire current loop interface through interfaces RS-232, RS-485 (2 wires).
HY dispenser interface converter
HY 4-wire interface converters (RS-485/RS-232 to 4-wire current loop and backwards) are intended for communication with dispensers (HongYang, Star) using 4-wire current loop interface through interfaces RS-232, RS-485 (2 wires).
NP dispenser interface converter
NP 4-wire interface converters (RS-485/RS-232 to 4-wire current loop and backwards) are intended for communication with dispensers Nuovo Pignone using 4-wire current loop interface through interfaces RS-232, RS-485 (2 wires).
LP dispenser interface converter
LP 3-wire interface converter (RS-485/RS-232 to 3-wire current loop and backwards) is intended for communication with fuel dispensers ( Logitron, Emgaz Dragon, Gilbarco Marconi, Fornovo LPG, others), which use 3-wire current loop interface, through interfaces RS-232, RS-485 (half-duplex).
NZ dispenser interface converter
NZ 2-wire interface converters (RS-485/RS-232 to 2-wire current loop and backwards) are intended for communication with dispensers (Actronic, Agira, Batchen, Compac, Intermech, PEC (Gallagher Fuel Systems), others) using 2-wire current loop interface through interfaces RS-232, RS-485 (2 wires).
NA dispenser interface converter
Dispenser interface converter NA (RS-485/RS-232 to non-addressable RS-422/RS-485/RS-232 and backwards) are intended for communication with fuel dispensers Censtar, which do not have a communication address in communication protocol and use one of the following interfaces (RS-422, RS-232, RS-485).
Wireless interface converter RFC
RFC converter is appointed for establishing of wireless communication between devices having interfaces RS-232 and RS-485.
Controller over mechanical fuel dispensers
Mechanical fuel dispenser controller is used in conjunction with a control system for petrol station to provide direct control over operation of electronic and mechanical fuel dispensers by controlling dispenser’s internal resources: motor, pulse sensor, nozzle, slowdown valve.
USB to RS-232 interface converter
USB to RS-232 interface converter is intended for conversion from USB interface (USB 1.1, USB 2.0) into two independent RS-232 interfaces in duplex and half-duplex modes of data exchange.